Here what i have.
in my panel box, Highrise i have one big breaker for 220 stuff, ok he has it hooked up like this . green wire to a brass screw on the side, then a black and white wire goes in each of the holes in the back of the breaker. then snapped it in place and flipped it on. is this right. or wrong, looks like it would be right .