bluesman...........you do not understand the intent of what I am doing.......I fully understand that that my set-up is not to the NEC or any other code. What I am doing is being creative the same way as many on this site are doing with cars............mixing and matching parts and solutions to produce something that works and is safe. I fully appreciate your knowledge of the electrical code but I am showing my temporary solution to the fact that I don't have space in my main panel for another line.
To cut through all the BS....................bottom line from MY perspective...........a #10 wire carries 30 amps safely.....solid or stranded, regardless of sheathing.......show me the ENGINEERING REASON, how 30A or 20A is different from a dryer, welder, compressor or heater (other than duty cycle). The code as you state says that a cord for a dryer must be used soley for a dryer but I say that # 10 is #10 and it don't make a damn bit of difference what is on the other end (assuming of course the draw is 30A or less). I am simply using an electrical cord designed to bolt up to to a specific application and ADAPTING it for use with another, similar to what many are doing with cars. I say that as long as wire size and connections are correct what I have is safe. However, I am open to any engineering evidence that says otherwise.
Last edited by scotzz; 01-19-2009 at 05:42 AM.